Magnetic hermetic control button EX VK200 (explosion protection marking 0EX IA IIC T6… T5 GA X / 1EX MB IIC T6… T5 GB X) PASHK.425411.152 TU
- 6836.69 PHP/pcs - from 10 pcs
- Invoice payment,
- Cash on delivery
- In detail
- Customer pickup,
- Transport company
- In detail
- BrandНПП «МАГНИТО-КОНТАКТ»
- Country of manufactureRussia
Declaration of conformity to the requirements of the Technical Regulations of the Customs Union "On the safety of low - voltage equipment" (TR CU 004/2011), the Technical Regulations of the Customs Union "Electromagnetic compatibility of technical means" (TR CU 020/2011) EAEU N RU D - RU. НР15.V. 08437/20 . Valid from 5.10.2020 to 4.10.2025
1.1. Magnetic hermetic control button Ex BK200 (button) is intended for use in security systems of objects as a control device for various equipment.
1.2. Ex BK200 (button) is marked 0Ex ia IIC T6 . . . T5 Ga X / 1Ex mb IIC T6 . . . T5 Gb X. . . In terms of explosion protection, Ex VK200 (button) meets the requirements of TR CU 012/2011 "On safety of equipment for work in explosive atmospheres", GOST 31610.0 - 2014 (IEC 60079 - 0: 2011) "Explosive atmospheres. Part 0. Equipment. General requirements ", GOST 31610.11 - 2014 (IEC 60079 - 11: 2011)" Explosive atmospheres. Part 11. Equipment with the type of explosion protection "intrinsically safe electrical circuit" i ", GOST R IEC 60079 - 18 - 2012" Explosive atmospheres. Part 18. Equipment with type of explosion protection sealing with compound "m". The "X" sign following the explosion protection marking means that the buttons are made with a permanently connected cable and indicates the need for a corresponding connection of the free end of the cable, clause 14.1 of GOST 31610.0 - 2014 (IEC 60079 - 0: 2011).
1.3. The buttons can be installed in rooms containing explosive mixtures of gases and vapors with air of category IIB, IIC, according to GOST IEC 60079 - 10 - 1 - 2011, GOST R IEC 60079 - 20 - 1 - 2011, other regulatory documents regulating the use of electrical equipment in explosive areas.
1.4. Ex BK200 (push button) has a normally open reed switch contact and a built - in LED indicator controlled from an external controller. The button is available with a permanently attached cable in two versions:
|option A||with cable outlet through a hole in the base of the housing (axial) - for hidden installation|
|option R||with a radial cable outlet in a metal hose of the MRPI - 6 type|
1.5. Ex BK200 designation (button) when ordering and in the design documentation of other products consists of the name, order code, designation TU. The order code identifies the cable outlet modification and is chosen by the customer.
Example of order: Ex VK200 (push button) option A PASHK.425411.152TU (with this order code, a push button will be supplied with a cable outlet through a hole in the base of the housing and a 1m length of the outlet) Other lead lengths are agreed by the consumer separately.
2. Main technical characteristics
|Overall dimensions, mm||Ø50 x 42 mm|
|Cable length Ex BK200 (button) in basic configuration||1m *
( * - at the request of the consumer, buttons are made with any output length)
|Weight Ех VK200 (button) in basic configuration with 1m cable (no more than), kg||0.5|
|Кнопки выпускается в климатическом исполнении УХЛ3.1 по ГОСТ 15150. Допускается эксплуатация в расширенном диапазоне при температуре от минус 40°С до плюс 60°С (температурный класс Т6), от минус 40°С до плюс 95°С (температурный класс Т5) и при относительной влажности воздуха до 93% при температуре плюс 40°С.|
|Атмосферное давление, кПа||от 84 до 106.7|
|Средний срок службы||не менее 8 лет|
|Степень защиты обеспечиваемая оболочкой по ГОСТ 14254||IP66/IP68|
|Усилие нажима при замыкании контактов не более||3.0 кгс|
|Электрические параметры геркона:
ток - не более 0.5 А,
напряжение - не более 100 В,
мощность - не более 10 Вт
Количество срабатываний - 1 х 106
|Параметры искробезопасной цепи:
- напряжение Ui, В
- ток Ii, А
- мощность Pi, Вт
- внутренняя индуктивность Li, мкГн
- внутренняя емкость Ci, пФ
|The supply voltage of the built - in indicator is from 12 to 24 V. The current consumption of the indicator is not more than 6.0 mA.|
|In the switching circuit, the button has a built - in fuse with Inom. = 0.5 A with a permissible short - circuit current of the external power supply Isc = 1.5 A and a fuse operation time of 0.2 s.|
|The button does not contain precious metals (clause 1.2 of GOST 2.608 - 78).|
3. Scope of delivery
|Magnetic hermetic control button Ех VK200 (button)||1 PC|
|screw М4х25 DIN 912 for a hex key||2 pcs|
|hex key||1 PC|
4.1. The marking is applied to the case of Ex BK200 (button) and contains:
- manufacturer's trademark
- device name
- values of switching parameters and permissible short - circuit current
- Climatic performance
- name of the certification body and number of the certificate
- serial number and production date
- special Ex marking and conditions of use
- degree of protection provided by enclosure IP66 / IP68
- special explosion - proof sign
- product circulation mark on the market of the Customs Union
5. Completeness of delivery
5.1. Ex BK200 (push button) has a normally open reed switch contact and a built - in LED indicator controlled from an external controller. The button is available with a permanently attached cable in two versions:
- option A: with cable outlet through a hole in the base of the housing (axial) - for concealed installation
- option R: with a radial cable outlet in a metal hose of the MRPI - 6 type.
5.2. In the switching circuit, the button has a built - in fuse with Inom. = 0.5 A with a permissible short - circuit current of the external power supply Isc = 1.5 A and a fuse operating time of 0.2 s.
5.3. The electronic components of the button are sealed from the external environment with a heat - resistant compound.
5.4. The buttons are produced in climatic version UHL3.1 in accordance with GOST 15150.
5.5. By the method of protection against electric shock, the device corresponds to class I in accordance with GOST 12.2.007.0. The button housing is equipped with an external grounding element.
5.6. Overall and mounting dimensions are shown Ex BK200 (button) in Fig. 1
Fig. 1 Overall and connecting dimensions of KM - 1
6. Ensuring explosion protection
6.1. Electrical elements of buttons and connections, spark - proof elements of an intrinsically safe circuit are isolated from an explosive atmosphere by pouring a compound in accordance with the requirements of GOST 31610.11 - 2014 (IEC 60079 - 11: 2011), GOST R IEC 60079 - 18 - 2012 and are placed in a case of stainless steel grade 12X18H10T . . .
6.2. Electric clearances, creepage distances and dielectric strength of insulation meet the requirements of GOST 31610.11 - 2014 (IEC 60079 - 11: 2011).
6.3. The design of the button is made taking into account the general requirements of GOST 31610.0 - 2014 (IEC 60079 - 0: 2011) for electrical equipment located in hazardous areas, has a permanently connected cable. The body of the button provides the degree of protection of the enclosure IP66 / IP68 in accordance with GOST 14254 2015 (IEC 60529: 2013).
6.4. The button does not contain electrical elements capable of storing energy dangerous for igniting gases of category IIB, IIC. Frictional and electrostatic intrinsic safety of the button body is ensured by the choice of construction materials and complies with GOST 31610.0 - 2014 (IEC 60079 - 0: 2011).
6.5. The maximum heating temperature of the surface of the button bodies does not exceed the permissible values for temperature classes T6 . . . T5 in accordance with GOST 31610.0 - 2014 (IEC 60079 - 0: 2011). The working temperature of the compound corresponds to the operating conditions. The mechanical and electrical properties of the compound provide explosion protection parameters in accordance with GOST R IEC 60079 - 18 - 2012.
6.6. The button body has the necessary inscriptions, explosion protection marking and an "X" sign.
6.7. Explosion protection provided with one damage inside.
7.1. The buttons refer to explosion - proof electrical equipment of group II in accordance with GOST 31610.0 - 2014 (IEC60079 - 0: 2011) and are intended for use in hazardous areas in accordance with the established explosion protection marking, the requirements of TR CU 012/2011, GOST IEC 60079 - 14: 2011, and other regulatory documents regulating the use of electrical equipment in explosive atmospheres.
7.2. Possible explosive areas of application, categories of explosive mixtures of gases and vapors with air in accordance with GOST IEC60079 - 10 - 1 - 2011, GOST R IEC 60079 - 20 - 1: 2011 and other documents.
7.3. Maintenance of sensors should be carried out in accordance with the requirements of GOST IEC 60079 - 17: 2013. “Explosive environments. Part 17. Inspection and maintenance of electrical installations ".
8. Instructions for assembly and installation
8.1. Operating conditions and installation of the Ex VK200 button (button) must comply with the requirements of GOST IEC 60079 - 14: 2011 and other regulatory documents regulating the use of equipment in hazardous areas.
8.2. The button is attached with screws or self - tapping screws to the installation site, according to Fig. 1
8.3. Connection to the button of the grounding conductor is made with the screw supplied
8.4. The color coding of the terminals and the designation of the circuits are shown in Fig. 2
8.5. In the button version A, the connected cable is led out of the housing through a hole in the base. This version is used when hidden cable routing to the button is required. In the R version of the button, the connected cable is led out of the case in a metal hose in a PVC sheath, type MRPI - 6.
Fig. 2. Ex BK200 terminal marking (button)
9. Warranty obligations
9.1. The manufacturer guarantees the compliance of the detectors with the requirements of the PASHK.425411.152 TU technical conditions, provided that the consumer observes the rules of storage, transportation and operation.
9.2. The warranty period for Ex VK200 (button) is 1 year from the date of commissioning, but no more than 2 years from the date of manufacture.